Don't risk an oil spill - if you are in any doubt, replace consumable items.
Flexible oil pipes should be inspected during every service visit and in the interests of safety, changed at regular intervals. There are different types of flexible oil pipe available and guarantee periods can be as short as one year. Where flexible oil pipes are marked with a date stamp, the age of the oil pipe should be established and if out of its guarantee period, replaced immediately.
Where no date stamp is visible or where an oil pipe is kinked, damaged or any doubt exists as to its integrity until the next service visit, it is recommended that it is replaced at the time of the service. Caution should be exercised to capture any oil lost during the disconnection of the oil line(s).
Consumable items such as nozzles, filter elements and flexible fuel lines should be replaced at least annually, or not later than the expiry of the manufacturer’s guarantee period. Where a customer refuses to have consumable items replaced as part of a routine service visit, this should be recorded on the CD/11 form and a warning label attached to the appliance identifying that either an immediate or potential risk is now present.
This advice can also be found in the OFTEC Technical Book 2.
For more technical advice, log into the website here and visit the technician hub pages. You'll find past copies of E-News, Oil Installer, technical book updates, information on the range of benefits you get as a registered technician and much more.
To register for an account on this website click here.
Click here to access the portal, you can also renew your registration or update your contact details through the portal.
Our technical team are available to answer any queries you have on building regulations, installation best practice, servicing and repairs.
Click here to contact us.